Abstract
In this study, the wind speed characteristics and energy potential in three selected locations in the southeastern part of Nigeria were investigated using wind speed data that span between 24 and 37 years and measured at a height of 10 m. It was shown that the annual mean wind speed at a height of 10 m for Enugu, Owerri and Onitsha are 5.42, 3.36 and 3.59 m/s, respectively, while the annual mean power densities are 96.98, 23.23 and 28.34 W/m^{2}, respectively. It was further shown that the mean annual value of the most probable wind speed are 5.47, 3.72 and 3.50 m/s for Enugu, Owerri and Onitsha, respectively, while the respective annual value of the wind speed carrying maximum energy are 6.48, 4.33 and 3.90 m/s. The performance of selected commercial wind turbine models (with rated power between 50 and 1,000 kW) designed for electricity generation and a windmill (rated power, 0.36 kW) for water pumping located in these sites was examined. The annual energy output and capacity factor for these turbines, as well as the water produced by the windmill, were determined. The minimum required design parameters for a wind turbine to be a viable option for electricity generation in each location are also suggested.
Background
The quest to reduce environmental impacts of conventional energy resources and, more importantly, to meet the growing energy demand of the global population had motivated considerable research attention in a wide range of environmental and engineering application of renewable form of energy. It is recognized that wind energy, as a renewable energy source, has stood out as the most valuable and promising choice. Wind energy by nature is clean, abundant, affordable, inexhaustible and environmentally preferable. Due to its many advantages, wind energy has also become the fastest growing renewable source of energy in both developed and developing countries. For example, wind energy is widely used to produce electricity in countries like Denmark, Spain, Germany, USA, China and India. Interestingly, the global cumulative installed capacity of wind power had increased sharply from 6,100 MW in 1996 to about 237,669 MW in 2011 [1]. In Africa, for example, Egypt, Morocco and Tunisia are the leading countries with installed capacities of 550, 291 and 114 MW, respectively, at the end of 2011 [1].
The increasing energy demand, the rapidly depleting fossil fuel reserves and the environmental problems associated with the use of fossil fuel have necessitated the development of alternative energy sources like wind energy for electricity generation in Nigeria. It is reported that the electricity production in Nigeria as of the end of 2010 is less than 4,000 MW due to fluctuations in the availability and maintenance of production sources, leading to a shortfall in supply [2]. However, analyses of available wind data for selected cities have confirmed a high prospect of wind energy resources in Nigeria. Several studies on renewable sources of energy have also been performed. A detailed review and discussion of these studies can be found in [2–6] and are not repeated here. Worthy of mention here from these studies, however, is that the effective utilization of wind energy at a typical location requires sound knowledge of the wind characteristics and accurate wind data analysis. For example, the choice of wind turbine design must be based on the average wind velocity at a selected wind turbine installation site [7]. Prior studies have also shown that the wind flow patterns are influenced by terrains, vegetation and water bodies.
Although several studies have been performed to investigate the characteristics and pattern of wind speed across Nigeria, less attention has been given to sites in the southeast region. According to [8, 9], the few reported studies on wind speed in this part of the country were limited to wind speed distributions, while less attention was paid to the wind energy potential evaluation. The focus of this study is, therefore, to evaluate the wind energy potential in three selected locations (Enugu, Owerri and Onitsha) in the southeast region and to assess the performance of selected small to mediumsize commercial wind turbines. It is the authors' view that this information will be helpful to the government and any organization in making an informed decision with regard to investment in wind energy resource in this part of Nigeria.
Methods
The wind data used in this study were obtained from the Nigerian Meteorological Agency, Oshodi, Lagos. The geographical coordinates of the meteorological stations where the wind speed data were captured at a height of 10 m by a cupgenerator anemometer are given in Table 1. There are many sources of measurement uncertainty in cupanemometer measurements. The guidelines and steps necessary to minimize these errors are outlined in Manwell et al. [10]. Following the methodologies proposed and explained in the ISO guide [11] to the expression of uncertainty in measurement, the uncertainty in the mean velocities at 95% confidence level was determined to be ±2%. Monthly wind data that span between 24 and 37 years were obtained for Enugu, Owerri and Onitsha. The recorded wind speeds were computed as the mean of the speed for each month. It should be noted that using monthly wind speed has some limitations such as loosing extremely low or high wind speeds within the month as well as inability to observe diurnal variations in the wind speed. However, using monthly mean wind speed, which is mostly available for most locations, can be used to study the seasonal changes in wind speed and facilitates wind data analysis.
Frequency distribution and site wind speed parameters
Several mathematical models such as normal and lognormal have been used for wind data analysis. Prior studies have also shown that statistical methods such as the Weibull and Rayleigh distribution models can equally be used [12]. According to [13–15], the twoparameter Weibull probability distribution function is the most appropriate, accepted and recommended distribution function for wind speed data analysis. This is because it gives a better fit for measured monthly probability density distributions than other statistical functions [12, 15]. In addition, the Weibull parameters at known height can be used to estimate wind parameters at another height [13]. Therefore, the twoparameter Weibull probability density function was used in this study. In Weibull distribution, the variation in wind velocity is characterized by two parameter functions: the probability density function and the cumulative distribution. The probability density function f(V) indicates the probability of the wind at a given velocity V, while the corresponding cumulative distribution function of the velocity V gives the probability that the wind velocity is equal to or lower than V, or within a given wind speed range. The Weibull probability density function is given as, e.g., [12, 16]:
where f(V) = the probability of observing wind speed (V), k = dimensionless Weibull parameter and c = the Weibull scale parameter (in meter per second). The scale factor could be related to the mean wind speed through the shape factor, which determines the uniformity of the wind speed in a given site. The cumulative distribution F(V) is the integral of the probability density function, and it is expressed as, e.g., [12, 16]:
The monthly and annual values of Weibull parameters were calculated using standard deviation method. This method is useful where only the mean wind speed and standard deviation are available. In addition, it gives better results than graphical method and has relatively simple expressions when compared with other methods [13, 17, 18]. Moreover, it is unlike most of the other methods that may require more detailed wind data (which, in some cases, are not readily available) for the determination of the Weibull distribution shape and scale parameters. The shape and scale factors are thus computed from Equations 3 and 4 given by [13, 19]:
where σ is the standard deviation, V_{m} is the mean wind speed (in meter per second) and Ґ(x) is the gamma function, which is defined as [17, 19]:
Alternatively, scale factor can be determined from the following expressions given by [20]:
Equation 6 is used in this study to estimate the monthly and annual scale factors.
In addition to the mean wind speed, the other two significant wind speeds for wind energy estimation are the most probable wind speed (V_{F}) and the wind speed carrying maximum energy (V_{E}). They can be expressed respectively as [12, 21]:
The most probable wind speed corresponds to the peak of the probability density function, while the wind speed carrying maximum energy can be used to estimate the wind turbine design or rated wind speed. Prior studies have shown that wind turbine system operates most efficiently at its rated wind speed. Therefore, it is required that the rated wind speed and the wind speed carrying maximum energy should be as close as possible [16].
Extrapolation of wind speed at different hub height
In most cases, the available wind data are measured at a height different from the wind turbine hub height. It is noted that it is the wind speed at the hub height that is of interest for wind power application; therefore, the available wind speeds are adjusted to the wind turbine hub height using the following power law expression, e.g., [12]:
where V is the wind speed at the hub height h V_{o} is wind speed at the original height h_{o} and α is the surface roughness coefficient and is assumed to be 0.143 (or 1/7) in most cases. The surface roughness coefficient α can be determined from the following expression [22]:
Alternatively, the Weibull probability density function can be used to obtain the extrapolated values of wind speed at different heights. Since the boundary layer development and the effect of the ground are nonlinear with respect to wind speed, the scale factor c and form factor k of the Weibull distribution will change as a function of height by the following expressions [13]:
where c_{o} and k_{o} are the scale factor and shape parameter, respectively, at the measurement height h_{o}. The exponent n is defined as:
Mean wind power density and energy density
The mean wind power density can be estimated by using the following equation:
where P(V) = the wind power (in watt), P_{D} = the wind power density (watt per square meter), ρ = the air density at the site (assumed to be 1.225 kg/m^{3} in this study) and A = the swept area of the rotor blades (in square meter). Both the mean wind speed and power density are generally used to classify the wind energy resource (e.g., Pacific Northwest Laboratory (PNL) wind power classification scheme, Illica et al. [23]). However, the wind power density (wind power per unit area) based on the Weibull probability density function can be calculated using the following equation [24]:
The mean energy density (E_{D}) over a period of time T is the product of the mean power density and the time T, and it is expressed as:
Wind turbine energy output and capacity factor
A wind energy conversion system can operate at its maximum efficiency only if it is designed for a particular site because the rated power and cutin and cutoff wind speeds must be defined based on the site wind characteristics [12]. It is essential that these parameters are selected so that energy output from the conversion system is maximized. The performance of a wind turbine installed in a given site can be examined by the amount of mean power output over a period of time (P_{e,ave}) and the conversion efficiency or capacity factor of the turbine. The capacity factor C_{f} is defined as the ratio of the mean power output to the rated electrical power (P_{eR}) of the wind turbine [12, 20].
The mean power output P_{e,ave} and capacity factor C_{f} of a wind turbine can be estimated using the following expressions based on Weibull distribution function [12]:
where v_{c}v_{r} and v_{f} are the cutin wind speed, rated wind speed and cutoff wind speed, respectively. For an investment in wind power to be cost effective, it is suggested that the capacity factor should be greater than 0.25 [25].
Winddriven rotodynamic pumps
There are three types of windpowered pumping systems. They are the mechanicalpiston pump, the mechanicalair lift (rotodynamic) pump and the electrical pump. In general, the volume of water produced by rotodynamic and electrical pumps are considered to be more than that of a piston pump at the same wind speed regime. This is because there is a better match between the rotodynamic and electrical pumps and the wind rotor than for a piston pump [26, 27]. In this study, the performance of a rotodynamic pump is simulated. For a rotodynamic pump driven by a wind turbine with a given cutin wind speed and a cutout wind speed, the water produced over a period of time T can be determined from:
where Q(V) is the discharge of the pump at any wind speed, and it is given by [28]:
where V_{d} is design wind speed, G is the gear ratio, N_{PD} is the speed of the pump at design condition, D is the wind turbine rotor diameter and λ_{D} is the design tip speed ratio of the wind turbine. For a waterpumping application, a tip speed ratio between 1 and 3 is recommended [10]. By substituting Equation 20 into Equation 19 and assuming Rayleigh probability density function f(V), the total water produced over a given time is expressed as [26]:
Results and discussion
Wind speed frequency distribution
The annual probability density frequency and cumulative distributions of wind speed for the three locations obtained using the Weibull distribution function are shown in Figure 1. The probability density function is used to illustrate the fraction of time for which given wind speed possibly prevails at a location. As expected, the peak of the density function frequencies of all the sites skewed towards the higher values of mean wind speed (Figure 1a). It should be remarked that the peak of the probability density function curve indicates the most frequent velocity. It can be observed from Figure 1a that the most frequent wind speed expected in Enugu, Owerri and Onitsha are about 5.5, 3.5 and 3.5 m/s, respectively. It can be further observed that Enugu has the highest spread of wind speed toward high wind speed among the locations.
The cumulative probability distributions of the wind speed at all the study locations (Figure 1b) show a similar trend. The cumulative distribution function can be used for estimating the time for which wind speed is within a certain speed interval. For wind speeds greater or equal to 2.5 m/s cutin wind speed, Enugu, Owerri and Onitsha have frequencies of about 96.9%, 86.5% and 86.9%, respectively, while the same locations respectively have frequencies of about 88.4%, 44.7% and 55.3% for wind speed of 3.5 m/s cutin wind speed. According to Ojosu and Salawu [3], if a wind turbine system with a design cutin wind speed of 2.2 m/s is used in these sites for wind energy resource for electricity generation, all the sites will have frequencies of more than 92%.
Mean wind speed and mean power density
The monthly variation of the mean wind speed characteristics (V_{m}, V_{F} and V_{E}), mean power density and mean energy density as well as the annual values of these parameters at a height of 10 m are presented in Tables 2, 3 and 4.
The monthly mean wind speed varies between 4.13 m/s in November and 6.30 m/s in March for Enugu site (Table 2). The monthly mean power density varies between 43.15 W/m^{2} in November and 153.16 W/m^{2} in March. Therefore, based on PNL wind power classification scheme [23], the monthly mean power density mostly falls into class 1 (P_{D} ≤ 100) except in January, February, April and July, when it falls into class 2 (100 < P_{D} ≤ 150), and in March, when it falls into class 3 (150 < P_{D} ≤ 200). However, the annual mean power density for this site is 96.98 W/m^{2} (class 1). For Owerri (Table 3), the minimum and maximum values of the monthly mean wind speeds are 2.72 and 3.70 m/s, respectively, while the annual mean wind speed for this site is 3.36 m/s. The monthly mean power density varies between 11.66 W/m^{2} in November and 31.02 W/m^{2} in January. The monthly mean power density falls into class 1 wind resource category (P_{D} ≤ 100) in all the months, and the annual mean power density for this site is 23.23 W/m^{2} (class 1). In the case of Onitsha (Table 4), the minimum and maximum values of the monthly mean wind speeds are 3.01 m/s (in November) and 4.23 m/s (in March), respectively. The monthly mean power density varies between 16.70 W/m^{2} in November and 46.36 W/m^{2} in March. The monthly mean power density falls into class 1 wind resource category (P_{D} ≤ 100) in all the months, and the annual mean power density for this site is 28.34 W/m^{2} (class 1). Detailed information about these sites' wind speed characteristics (mean wind speed, most probable wind speed (V_{F}) and the wind speed carrying maximum energy (V_{E})) and mean power density are illustrated in Tables 23 and 4.
The least monthly value of the Weibull shape parameter k for Owerri is 2.61 in January and reached the highest value of 8.48 in the month of May. Therefore, the wind speed is most uniform in Owerri in May, while it is least uniform in December. The annual shape factors for Enugu, Owerri and Onitsha are 4.05, 5.10 and 4.27, respectively. The least monthly value of Weibull scale parameter c is obtained as 2.97 m/s in the month of November in Owerri, and the highest value of 6.81 m/s in the month of March in Enugu. The annual shape factors for Enugu, Owerri and Onitsha are 5.87, 3.65 and 3.96 m/s, respectively.
In summary, Enugu has the highest annual mean wind speed among the sites considered in this study. Also, this site has the highest values of annual power density. Even though the most probable wind speed (V_{F}) is a statistical characteristic, which may not be directly connected to wind energy [21], it does not necessarily mean that Enugu has much higher wind potentials than the other locations considered. However, as mentioned earlier, the efficiency of a wind turbine is closely related to these parameters, especially V_{E}, which should be as close as possible to the design or rated wind speed of the system. Therefore, the proposed wind turbine, if installed in Enugu, would likely produce more power than other locations. Moreover, it can be considered as the best site for wind energy development in southern Nigeria (based on the three sites considered in this study). Furthermore, the monthly mean wind speeds in south Nigeria ranges from 2.72 to 6.30 m/s. The monthly mean power density varies between 11.66 and 153.15 W/m^{2}, while the annual mean power density is in the range of 23.23 to 96.98 W/m^{2}. It can be inferred from this analysis that the wind resource in this part of Nigeria can be classified mostly into class 2 or less category. Furthermore, the annual mean energy density varies between 203.53 and 717.62 kWh/m^{2}.
Even though the wind resource in these locations falls into class 2 or less, which is considered as marginally or unsuitable for wind power development, the wind power can be used for water pumping and smallscale electricity generation, providing intermittent power requirements for a variety of purposes that need lowenergy capacity, slowrunning hightorque wind turbines with multiblade, e.g., [3, 4, 6, 29]. For a modern wind turbine, the cutin wind speed required by it to start generating electricity is generally between 3 to 5 m/s. Depending on the size of the turbine, the peak power output can be attained when the wind speed (rated wind speed) is in the range of 10 to 15 m/s [6]. For water pumping, wind turbine can be operated at a lower wind speed; however, they can function effectively when the wind speed is more than 3 m/s. Based on the required quantity of water, a site with a mean wind speed around 2.0 m/s can be considered for windpowered pump application [30]. Similarly, depending on the end use of the generated power, it can be concluded that these locations may be suitable for utilization of wind energy.
Performance of selected wind turbines
Seven small to mediumsize commercial wind turbine models with rated power range from 50 to 1,000 kW [31–33] were selected to simulate their performance at Enugu, Owerri and Onitsha. These are P1550, P19100, P50500 and P621000 models (Polaris America LLC, Lakewood, NJ, USA ); WES30 model (Wind Energy Solutions BV, The Netherlands); WWD160 model (Winwind, Espoo, Finland) and BONUS 1000–54 (Siemens AG, Erlangen, Germany). The selected wind turbine models and their characteristic properties are given in Table 5. For each location, the annual energy output and capacity factor based on Weibull distribution function parameters at their respective hub height are determined using Equations 17 and 18, respectively.
The performance of the selected wind turbine models at all the locations is presented in Figure 2. The figure clearly reveals that irrespective of the wind turbine model, Enugu seems to be the best site for wind power development for electricity generation. This is expected because, when compared with other sites, Enugu has the highest annual mean wind speed and highest value of V_{E} at the hub height for each turbine. The annual energy output for Enugu ranges from about 113 MWh/year using POLARIS 19–100 model to 2,444 MWh using WWD160 model. Among the 1,000kW model turbines, the WWD160 model produced the highest power output, closely followed by the POLARIS 62–1000 (2,431 MWh/year), while BONUS 1000–54 produced the least power (849 MWh/year). This observed trend is related to the hub height and rotor diameter (which are lowest for the BONUS model), the design or rated wind speed (highest for the BONUS model, 14 m/s) and the cutin wind speed (highest for the WWD160 model, 3.6 m/s). Even though the hub height of the WWD160 model is higher than that of the POLARIS 62 model, the POLARIS 62 model still produced almost the same amount of power (2,431 MWh/year) due to its lower cutin wind speed and rated wind speed. Furthermore, it is observed that the energy output from the POLARIS 15–50 model is slightly more than the power output from the POLARIS 19–100 model. This is because both models have the same hub height, and the POLARIS 19–100 model has higher rated wind speed than the POLARIS 15–50 model.
The minimum annual energy outputs of 6.05 and 18.83 MWh/year are observed for Owerri and Onitsha, respectively, using the P19100 model. While the maximum annual energy outputs are 178.58 and 461.32 MWh/year, respectively, for Owerri and Onitsha with the WWD160 model. For each of these sites, the power generated by each wind turbine follows the same trend observed in Enugu. Regardless of the location, the WWD160 wind turbine model produced the highest quantity of annual energy output. For example, if 1,000kW turbines are to be operated at the same hub height, the POLARIS 62–1000 will likely perform better than WWD160 and BONUS100054 because of its low cutin wind speed and rated wind speed as well as its bigger rotor diameter compared with other models.
The cost effectiveness of a wind turbine can be roughly estimated by the capacity factor of the turbine. This factor is a useful parameter for both consumer and manufacturer of the wind turbine system [24]. The WWD160 model has the highest value among the models considered for all the sites. The C_{f} values for this model are 27.90%, 2.04% and 5.27% for Enugu, Owerri and Onitsha, respectively. The C_{f} values for Enugu for POLARIS 15–50, POLARIS 62–1000 and WWD160 are 28.30%, 27.75% and 27.90%, respectively. These values are greater than the suggested recommended value before an investment can be considered worthwhile. Hence, these wind turbines or similar turbine model will be good for electricity generation in Enugu. In Owerri, however, the capacity factor for other wind turbine models ranges from 0.49% for the BONUS100054 model to 2.04% for the WWD160 model. Similarly, the minimum and maximum capacity factors at Onitsha are 1.62% for the BONUS100054 model and 5.27% for the WWD160 model, respectively. Therefore, these two sites may be considered for wind energy development for smallscale applications such as water pumping (see ‘Windpowered pumps performance’). It should be noted that the cost of generating electricity using wind turbine is inversely proportional to the capacity factor. The higher the capacity factor (or higher wind speed regime), the lower the cost of generated electricity, assuming that all factors remain the same (see, e.g., Paul et al. [34]).
Based on the annual energy output and the capacity factor, the POLARIS 62–1000 and WWD160 models or wind turbines with similar designed characteristics will be best suited for electricity generation at Enugu and smallscale application in other locations. However, by redesigning the selected wind turbine models to operate at lower cutin wind speed (especially the WWD160 and BONUS10054 models), lower rated wind speed (especially BONUS10054) and higher hub height compared with their current design parameters (cutin and rated wind speeds and hub height), both the annual energy output and capacity factor could significantly be improved. For instance, if POLARIS 62–1000 is to be operated at a hub height of 70 m and rated wind speed of 10 m/s, the capacity factor for Enugu, Owerri and Onitsha will be 59.17%, 8.20% and 16.99%, respectively. However, increasing the hub height may increase the overall capital cost of the wind turbines. But this is compensated for by increased in capacity factor and, hence, the energy output from the wind turbines.
In order to meet the minimum recommended capacity factor (25%) for electricity generation, the following design parameters are suggested: wind turbine model with a minimum hub height of 55 m, cutin wind speed of less than 3.5 m/s, rated wind speed of around 12 m/s and cutout wind speed of 25 m/s are recommended for Enugu; for Owerri, wind turbine with a minimum height of 75 m, cutin wind speed of less than 3.5 m/s, rated wind speed of around 8.5 m/s and cutout wind speed of 20 m/s are recommended; while a system with a minimum hub height of 65 m, cutin wind speed of less than 3.5 m/s, rated wind speed of around 9 m/s and cutout wind speed of 20 m/s are recommended for Onitsha.
Windpowered pumps performance
In this section, the performance of windpowered pumps assumed to be located in each of the locations considered in this study is presented and discussed. For the performance assessment, a wind turbine model with a rated power of about 0.36 kW is chosen. The characteristic properties of this wind turbine model and the specifications of the pumps are given in Table 6. The wind turbine characteristics are similar to the FT2.5 wind turbine model (produced in China, according to [35]) [35, 36] for water pumping. The hub height of the wind turbine is assumed to be 15 m, which is within the hub height range for common commercial wind turbines for waterpumping application [30]. The pump head of 10 m is used for the analysis. This pump head was chosen because it is within the range of the water table level of 3 to 20 m in this part of Nigeria [37] and within the range of the design lifting height of 5 to 10 m for the FT2.5 windmill [35]. The monthly mean wind speeds at hub height at each selected site are computed using Equations 9 and 10. The quantity of water pumped per month is computed using Equation 23. This equation was solved using Wind Energy Resource Analysis software developed by Mathew [25]. The software is based on Rayleigh distribution function and requires the mean wind speed, wind turbine and pump parameters as inputs.
The comparison between water produced per month by rotodynamic pump at the three locations is presented in Table 7. As expected from the wind speed frequency distribution, the amount of water output from the pump at Enugu is highest among the three locations. In Enugu, the monthly water output varies between about 3,136 and 3,512 m^{3}, and the average volume discharge is about 3,442 m^{3}/month. In Owerri, where the pump has the least performance among the three sites, the monthly water output varies between 1,936 and 2,844 m^{3} with an average discharge volume of about 2,530 m^{3}/month. In the case of Onitsha, the monthly water output varies between about 2,206 and 3,194 m^{3}, and the average volume discharge is about 2,730 m^{3}/month. Therefore, all the sites have strong potential for wind energy development for water pumping. In fact, wind resource in these sites could also be used for electricity generation, as previously shown.
The total numbers of habitants that can be served by water discharged from these sites are also shown in Table 7. Based on water usage of 36 L/capita/day in Nigeria as of 2006 [38], the water output at Enugu can serve between 2,900 and 3,250 habitants depending on the month. The average number of people that can be served per month is estimated to be around 3,190. However, if the estimate is based on the minimum recommended water usage of 50 L/capita/day [38], the water produced can only serve about 2,290 habitants per month on average. In Owerri, the water produced can serve about 2,340 and 1,690 habitants per month on average based on 36 and 50 L/capita/day, respectively, while the total numbers of habitants that can be served by the water produced in Onitsha are 2,530 and 1,820/month on average based on water usage of 36 and 50 L/capita/day, respectively. Therefore, for small rural communities scattered across the southeastern part of Nigeria where access to good water and unreliable supply of water is a regular problem, wind resource development for water pumping will be a good option. For a larger community, the performance of a pump can be increased if a wind turbine with higher rated power (or diameter) is used instead of the small size used in this study. In addition, two or more wind turbines can be installed in these sites in order to increase the quantity of water produced.
Conclusions
In this study, the wind speed and wind energy potential in selected three locations in the southeastern part of Nigeria were investigated. In addition, the performance of selected commercial wind turbine models designed for both electricity generation and water pumping located in these sites was investigated. The findings from this study can be summarized as follows:

1.
The annual mean wind speeds for Enugu, Owerri and Onitsha are 5.42, 3.36 and 3.59 m/s, respectively. The annual values of the wind speed carrying maximum energy for these locations are respectively 6.48, 4.33 and 3.90 m/s.

2.
The mean annual value of Weibull shape parameter k is between 4.05 and 5.10, while the annual value of scale parameter c is between 3.96 and 5.87 m/s.

3.
The annual mean power density for Enugu, Owerri and Onitsha are 96.98, 23.23 and 28.34 W/m^{2}, respectively. Therefore, based on the wind data used in this study, the wind energy resource in southeast Nigeria may generally be classified into class 1. However, based on monthly mean power density, the wind resource may fall into higher class category in some cases.

4.
Based on the capacity factor, the POLARIS 15–50, POLARIS 62–1000 and WWD160 models or wind turbines with similar designed characteristics will be best suited for electricity generation in Enugu. However, in order to meet the minimum recommended capacity factor (25%) for electricity generation, wind turbine models with cutin wind speed of less than 3.5 m/s minimum and hub height of 55, 75 and 65 m, as well as rated wind speed of about 12, 8.5 and 9 m/s, respectively, are recommended for Enugu, Owerri and Onitsha.

5.
Using a 0.36kW wind turbine, the average monthly water produced by a rotodynamic pump assumed to be installed in Enugu, Owerri and Onitsha is determined as 3,442, 2,530 and 2,730 m^{3}, respectively. The quantity of water can serve about 2,290, 1,690 and 1,820 habitants in respective locations.
Abbreviations
 A:

wind power rotor swept area
 c:

Weibull scale parameter
 Cf:

capacity factor
 CO:

scale factor at the height ho
 CP:

wind turbine power coefficient
 CPD:

wind turbine design power coefficient
 D:

wind turbine rotor diameter
 ED:

mean energy density
 f(V):

probability of observing wind speed (V)
 F(V):

cumulative of observing wind speed (V)
 G:

pump gear ratio
 g:

acceleration due to gravity
 H:

water head
 H:

wind turbine hub height
 ho:

cupgenerator anemometer height
 k:

dimensionless Weibull shape parameter
 ko:

shape parameter height ho
 NPD:

pump speed at design condition
 n:

exponent
 PD:

mean wind power density
 Pe:

ave: mean power output
 PeR:

rated wind turbine power
 P(V):

wind power
 Q:

water produced at a given time
 Q(V):

volume discharge of the pump at any wind speed V
 T:

period or time
 V:

wind speed
 VE:

wind speed carrying maximum energy
 VF:

most probable wind speed
 Vm:

mean wind speed
 Vo:

wind speed at the cupgenerator anemometer height
 vc:

cutin wind speed
 Vd:

vr, rated wind speed
 vf:

cutoff wind speed.
References
 1.
Global Wind Energy Council: Global wind report: annual market updates. (2011). Accessed 30 April 2012 http://www.gwec.net/
 2.
Fagbenle RO, Katende J, Ajayi OO, Okeniyi JO: Assessment of wind energy potential of two sites in NorthEast. Nigeria. Renew. Energy 2011, 36: 1277–1293.
 3.
Ojosu JO, Salawu RI: A survey of wind energy potential in Nigeria. Solar and Wind Technology 1990, 7: 155–67. 10.1016/0741983X(90)90083E
 4.
Adekoya LO, Adewale AA: Wind energy potential of Nigeria. Renew. Energy 1992, 2: 35–39. 10.1016/09601481(92)90057A
 5.
Fadare DA: The application of artificial neural networks to mapping of wind speed profile for energy application in Nigeria. Applied Energy 2010, 87: 934–942. 10.1016/j.apenergy.2009.09.005
 6.
Adaramola MS, Oyewola OM: On wind speed pattern and energy potential in Nigeria. Energy Policy 2011, 39: 2501–2506. 10.1016/j.enpol.2011.02.016
 7.
MarciusKaitis M, Katnals V, Karaliauskas A: Wind power usage and prediction prospects in Lithuania. Renew. Sustain. Energy Rev. 2008, 12: 265–277. 10.1016/j.rser.2006.05.012
 8.
Anyanwa EE, Iwuagwu CJ: Wind characteristics and energy potentials for Owerri Nigeria. Renew. Energy 1995, 6: 125–128. 10.1016/09601481(94)000285
 9.
Asiegbu AD, Iwuoha GS: Studies of wind resources in Umudike, south east Nigeriaan assessment of economic viability. J. Eng. Appl. Sci. 2007, 2: 1539–1541.
 10.
Manwell JF, McGowan JG, Rogers AL: Wind Energy Explained: Theory, Design and Application. 2nd edition. Wiley, Wiltshire; 2010.
 11.
International Standards Organisation: Guide to the Expression of Uncertainty in Measurement. 1st edition. 1992.
 12.
Akpinar EK, Akpinar S: An assessment on seasonal analysis of wind energy characteristics and wind turbine characteristics. Energy Conversion and Management 2005, 46: 1848–67. 10.1016/j.enconman.2004.08.012
 13.
Justus CG, Hargraves WR, Mikhail A, Graber D: Methods for estimating wind speed frequency distributions. J. Appl. Meteorol. 1978, 17: 350–353. 10.1175/15200450(1978)017<0350:MFEWSF>2.0.CO;2
 14.
Akdag SA, Dinler A: A new method to estimate Weibull parameters for wind energy applications. Energy Conversion and Management 2009, 50: 1761–1766. 10.1016/j.enconman.2009.03.020
 15.
Akdag SA, Bagiorgas HS, Mihalakakou G: Use of twocomponent Weibull mixtures in the analysis of wind speed in the Eastern Mediterranean. Applied Energy 2010, 87: 2566–2573. 10.1016/j.apenergy.2010.02.033
 16.
Mathew S, Pandey KP, Kumar AV: Analysis of wind regimes for energy estimation. Renew. Energy 2002, 25: 381–399. 10.1016/S09601481(01)000635
 17.
Jowder FAL: Wind power analysis and site matching of wind turbine generators in Kingdom of Bahrain. Applied Energy 2009, 86: 538–545. 10.1016/j.apenergy.2008.08.006
 18.
Kwon SD: Uncertainty analysis of wind energy potential assessment. Applied Energy 2010, 87: 856–865. 10.1016/j.apenergy.2009.08.038
 19.
Ouammi A, Dagdougui H, Sacile R, Mimet A: Monthly and seasonal assessment of wind energy characteristics at four monitored locations in Liguria region (Italy). Renew. Sustain. Energy Rev. 2010, 14: 1959–1968. 10.1016/j.rser.2010.04.015
 20.
Balouktsis A, Chassapis D, Karapantsios TD: A nomogram method for estimating the energy produced by wind turbine generators. Solar Energy 2002, 72: 251–259. 10.1016/S0038092X(01)000998
 21.
Bagiorgas HS, Assimakopoulos MN, Theoharopoulos D, Matthopoulos D, Mihalakakou GK: Electricity generation using wind energy conversion systems in the area of Western Greece. Energy Conversion and Management 2007, 48: 1640–1655. 10.1016/j.enconman.2006.11.009
 22.
Ucar A, Balo F: Evaluation of wind energy potential and electricity generation at six locations in Turkey. Applied Energy 2009, 86: 1864–1872. 10.1016/j.apenergy.2008.12.016
 23.
Ilinca A, McCarthy E, Chaumel JL, Retiveau JL: Wind potential assessment of Quebec Province. Renew. Energy 2003, 28: 1881–1897. 10.1016/S09601481(03)000727
 24.
Celik AN: A statistical analysis of wind power density based on the Weibull and Rayleigh models at the southern region of Turkey. Renew. Energy 2004, 29: 593–604. 10.1016/j.renene.2003.07.002
 25.
Mathew S: Wind Energy: Fundamentals. Resource Analysis and Economics, Springer, Heidelberg; 2006.
 26.
Mathew S, Pandey KP: Modelling the integrated output of winddriven rotodynamic pumps. Renew. Energy 2003, 28: 1143–1155. 10.1016/S09601481(02)001854
 27.
Hau E, Renouard R: Wind turbines: Fundamentals, technologies, applications, economics. 2nd edition. Springer, Heidelberg; 2006.
 28.
Mathew S, Pandey KP: Modelling the integrated output of mechanical wind pumps. J. Solar Energy Engineering 2000, 122: 203–206. 10.1115/1.1319498
 29.
Fagbenle RL, Karayiannis TG: On the wind energy resource of Nigeria. Intern. J. Energy Res. 1994, 18: 493–508. 10.1002/er.4440180502
 30.
Meel J, Smulders P: Wind Pumping: A Handbook (World Bank Technical Paper No. 101). World Bank, Washington; 1989.
 31.
Polaris (2011). Accessed 04 April 2011 http://www.polarisamerica.com/ (2011). Accessed 04 April 2011
 32.
Wind Energy Solutions (2011). Accessed 04 April 2011 http://www.wes30.com/ (2011). Accessed 04 April 2011
 33.
WinWinD (2011). Accessed 04 April 2011 http://www.winwind.com/Documents/Press%20Kit/wwd1.pdf (2011). Accessed 04 April 2011
 34.
Paul SS, Oyedepo SO, Adaramola MS: Economic assessment of water pumping systems using wind energy conversion systems in the southern part of Nigeria. Energy Exploration and Exploitation 2012, 30: 1–18. 10.1260/01445987.30.1.1
 35.
Shi J, Shen D, Wei J: The development of wind pumping technology in China. Biomass 1989, 20: 13–23. 10.1016/01444565(89)900176
 36.
Ltd Bobs Harries Engineering: Kijito wind pumps – Pumping water with wind: Information package. Brochure, Bob Harries Engineering Limited; 2009.
 37.
Adelana SMA, Olashinde PI, Bale RB: An overview of the geology and hydrogeology of Nigeria. In Applied Groundwater Studies in Africa. Edited by: Adelana S, MacDonald A. Taylor and Francis, London; 2008:171–197.
 38.
Programme United Nations Development: Human Development Report. United Nations Development Programme, New York; 2006.
Acknowledgments
The authors are grateful to the Nigerian Meteorological Agency (NIMET), Oshodi, Lagos, Nigeria, for providing data for this study.
Author information
Affiliations
Corresponding author
Additional information
Competing interests
The authors declare that they have no competing interests.
Authors’ contributions
SOO collected the wind data and carried out initial analysis. Wind turbine calculations were performed by MSA. ‘Background’ section was drafted by SSP. ‘Results and discussion’ section was jointly drafted by MSA and SSP. All authors read, edited and eventually approved the manuscript to be submitted.
Authors’ original submitted files for images
Below are the links to the authors’ original submitted files for images.
Rights and permissions
Open Access This article is distributed under the terms of the Creative Commons Attribution 2.0 International License ( https://creativecommons.org/licenses/by/2.0 ), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
About this article
Cite this article
Oyedepo, S.O., Adaramola, M.S. & Paul, S.S. Analysis of wind speed data and wind energy potential in three selected locations in southeast Nigeria. Int J Energy Environ Eng 3, 7 (2012). https://doi.org/10.1186/2251683237
Received:
Accepted:
Published:
Keywords
 Mean wind speed
 Wind power density
 Southeast Nigeria
 Electricity
 Water pumping